Mauldin SC Heating and Cooling
Primus Heating & Air Conditioning provides air conditioning repair, heating and furnace services to the residents of Mauldin, SC and the surrounding areas since 2004!
Read our reviews and find out why your neighbors consider us to be their nearby HVAC company in Mauldin, SC.
for Mauldin, SC
Quick response, great service
Chris - Mauldin, SC
Mark fit me into his schedule on short notice and had things up and running again in a matter of minutes. Affordable and friendly service.
Rachel - Mauldin, SC
Prompt, efficient, reasonably priced HVAC service. Highly recommend Primus! Mark is professional and knowledgeable.
Great, as always!
Kym E. - Mauldin, SC
I have been using Primus for years and never had bad or upsetting service.
Response from Primus Heating and Air Conditioning LLC:
Thank you so much for your kind words. It’s very nice to see kind words like that. Thank you again.
Customer stated that local gas company was called because of a gas smell. After the repair the gas company started the ICP gas package unit and they noticed the burners burning strangely. We noticed an object in one of the gas burner orifice. We pulled the burners and remove a dead bug lodged in one of the burner offices.
Gas package system
Customer stated their overflow pan was leaking in the attic area and onto their ceiling. Found man drain clogged and cleared drain and vacuumed water from overflow pan. Informed customer of a tune up of their system since it wasn't tune up in five years. Cleaned dirty condenser coil because of a very higher than usual condensing liquid pressure. Replaced a weak blower motor run capacitor. After cleaning pressure on high side lowered. Charged system with the correct amount of R-22 refrigerant.
Goodman Gas Package unit not heating. Found pressure switch open.
Heat pump package system. Ducting damaged by an animal in the crawl. Burnt element on the heater auxiliary kit.
Heat pump package system. Ducting was damaged by an animal. Heater auxiliary kit damaged.
Heat pump system transformer was shorted due to a mis wiring of the thermostat. Replaced wrong installed thermostat. Had to charge system with 2lbs of refrigerant.
Estimate to replace HVAC equipment and ducting.
Today we are inspecting an air conditioning and furnace operation. We are checking condition of the ducting and operating parameters of the air conditioning system. We are checking the operating parameters of a upflow gas furnace.